Pool pumps consume a vast amount of energy. To reduce costs associated with water circulation, Variable Frequency Drives are now available to lower consumption that also extend the pump’s motor life.
Variable frequency drives (VFD) allow the pump to run at its most efficient point and maintenance costs drop due to motor protection, motor soft start and a significant decrease in water hammer protecting the shaft and impeller.
Installing a VFD to your pump immediately lowers energy costs by 5 to 10 percent by simply dialing in the pump where it actually needs to be. VFDs do the following:
Step 1: Choose a VFD. All you need to know is the phase going to the pump — single or three; the voltage going from the power source to the VFD; the horsepower of the pump onto which you are installing the VFD, and whether the drive will be installed indoors and outdoors.
Step 2: Install the VFD. The incoming power from the power source basically gets wired to the incoming side of the VFD and then the pump motor gets wired to the outgoing part of the VFD.
Step 3: Ensure correct pump selection. Proper pump selection – sizing – and optimal flow rates are key to lowering energy usage. Many pool pumps are oversized by design and bigger than needed.
Even with the advantages explained, some find the cost of a VFD hard to justify. However, the price should be compared to the expense of doing nothing before ruling out a VFD.
For example, using a single-speed pump a facility might have operational costs of $900 per year. After five years, the facility will have spent $4,500 to operate the pump. Comparable operational costs with a VFD may be as little as $200 per year or less than a quarter the cost during the same five-year period.
To quantitatively work on reducing the pump operating costs, start by determining exactly what it costs to run your system. Determine the GPM (gallons per minute) and TDH (total dynamic head) of the pump, how long each day the pump runs, and what the cost per kilowatt hour your power company is charging. Once you have a clear dollar figure to tackle, you will find that adding a VFD is a no-brainer.
Mike Fowler is the commercial marketing and sales manager for Pentair Aquatic Systemsin Sanford, N.C. He has been with Pentair since 1992, starting his career in the technical services department at Purex Pool Products. Fowler has held many managerial roles within the company, including marketing, Customer management, accounting and products. He can be reached via e-mail at email@example.com. Visit pentair.com for more information.